The contractor who put the gate in under a government grant had undersized the 120 volt wire going to gate and over fused it. they also ran 22# gauge wire for the exiting and safety loops in ground 3 sizes too small it needed to be at least 14# gauge .
Then we found the wire going to the reader where you presented the card had been smashed and pinched which is why the gate stopped operating several months after it was installed. A totally incompetent install by a MBE qualified contractor and your tax payer dollars wasted and everyone just shrugs.
I have ordered and am now in process of installing a new parking gate.
|card reader not fastened properly and water intrusion|
|wires popping up out of asphalt|
|22# white burg wire not 14# traffic loop wire.|